Gas information sheet 10: Concealed locations for piping in high rise buildings
This gas information sheet provides information about:
- what constitutes a concealed location in a high rise building and the criteria it must meet to comply with the Australian standard.
- the requirements for piping in concealed locations (other than underground or embedded in concrete) as specified in AS/NZS 5601.1 Gas Installations: General installations, Clause 5.3.8 (Table 5.2).
Piping in a concealed location often remains undisturbed for long periods of time, which can allow leaks to go undetected. Without adequate ventilation, gas can build up to potentially dangerous levels over a period of time. Concealed locations are considered to be concealed even when accessible via an access panel or door.
There are three main types of concealed location:
- Pipe riser shafts.
- Service cupboards.
- Ceiling spaces.
Pipe riser shafts
Pipe riser shafts act like a chimney (referred to as stack effect or chimney effect) for leaking gas so must be designed and built to contain and vent potential gas leaks from non-permanent joints. A pipe riser shaft must be:
- sealed from adjacent areas
- well ventilated with a vent at the top and bottom of the shaft, and suitably sized floor penetrations that the pipe passes through (see the section on ‘Calculating the free ventilation area’ for information about how large these vents and penetrations must be)
- vented to a safe location outside the building.
Pipe riser shafts may contain equipment that must be accessible for servicing and inspection.
A service cupboard, which is typically installed on each floor level, is an area that conceals piping or equipment, is sealed to stop the migration of leaking gas into the building structure, and can be accessed via a service door. Service cupboards must also be well ventilated when non-permanent joints are being used.
Ceiling spaces can be difficult to ventilate and permanent joints should be used as much as possible. Ceiling spaces must be ventilated when non-permanent joints are installed.
One solution for isolating ceiling spaces that have non-permanent joints (for example, occupancy isolation valves) from the rest of the ceiling is to install a sealed box (with an access hatch incorporating a vent into the space below) to enclose the non-permanent joints.
See the section on ‘Calculating the free ventilation area’ for information about how large ceiling space and service cupboard vents must be.
What is required when operating pressures exceed 7 kPa?
When the operating pressure exceeds 7 kPa:
- pipe riser shafts, service cupboards, and ceiling spaces must all be ventilated (as already described)
- all piping joints must be permanent and the number of joints kept to a minimum
- piping must be accessible.
What is ‘accessibility’?
Accessibility generally refers to a location with sufficient clearances to allow access to, and removal of, all serviceable components.
In this case, it means that pipes and services can be accessed via a ceiling hatch or a sub-floor door, or are otherwise viewable and accessible on each floor of a high rise building.
Calculating the free ventilation area
The free ventilation area refers to the size of an opening for ventilation or a physical vent and is:
- calculated using AS/NZS 5601.1, Table 5.3
- based on the cross-sectional area of the pipe riser shaft, service cupboard, void, duct, box or sleeve being ventilated.
For example, for a pipe riser shaft with a cross-sectional area between 0.05 and 7.5 square metres, the minimum area of each floor penetration the pipe passes through must be 0.05 square metres.
Ventilation openings or physical vents must always be sized to provide the minimum required free ventilation area. Ventilation openings must also comply with the requirements of AS/NZS 5601.1, Clause 5.3.12.
What is a permanent joint?
This is a joint that cannot be easily disassembled. Examples include brazed, welded, crimped, and hydraulically or mechanically compressed joints. (See AS/NZS 5601.1, Clause 1.8.82.)
The use of a quick-setting thread compound is not considered to be a permanent jointing method.
Contact ESV’s Technical Information Line on 1800 652 563, or email email@example.com.
 A building with five or more storeys above ground level.
 Unless the pipe joints are permanent and the number of joints is kept to a minimum.
 This includes pressure regulators, limited flexibility connections, isolation valves, pipe anchors, and spring clips.