Gas information sheet 19: Second-hand commercial catering equipment
This information sheet has been prepared to advise gasfitters and buyers of their responsibilities for the purchase and installation of second-hand commercial catering equipment.
Energy Safe Victoria (ESV) is concerned that with the thriving market in second-hand commercial catering equipment some catering equipment has been found to be unsafe and many appliances do not meet minimum safety requirements, even though when new the appliance may have been certified.
Second-hand appliances can be purchased at lower costs which is an obvious attraction when setting up a business. Often these appliances are obtained at auction or from a dealer, and the age and condition of the appliances vary enormously.
It is an offence under the Gas Safety Act to sell or offer to sell an unsafe appliance. Appliances being sold for installation must be safe and comply with accepted standards.
AS/NZS 5601.1: 2013 Gas Installations, states:
Before a second-hand appliance is installed, the appliance shall satisfy the safety requirements of the Technical Regulator.
Second-hand commercial catering appliances should show a certification number indicating that when new the appliance complied with the required standard and was approved. If you are uncertain whether your appliance has certification, refer to the National Database for gas appliances, available at http://equipment.gtrc.gov.au.
Imported second-hand appliances
Any imported second-hand appliance must be referred to ESV before being installed. ESV will advise on the requirements for acceptance.
Failure to show proof of certification may result in gas supply being withheld. A second-hand appliance without an approval number may never have been submitted for testing and therefore ESV’s acceptance will be required. Where it cannot be established that an appliance has been certified, ESV will advise on the requirements for acceptance.
General safety requirements
|Type of appliance||Required gas safety features|
|All appliances||A flame safeguard system shall be fitted to:
Where the combustion air supply to a gas appliance is provided by mechanical means an interlock shall be installed to cause the gas supply to the appliance to be shut-off upon failure of the mechanical air supply system.
|Salamanders, grillers and toasters||Flame safeguard systems were not mandatory on new appliances until 2005 but must be operational if fitted.|
|Stockpots||Steam-jacketed stockpots shall have a low water level gas cut-off device.|
|Brat pans||Tilting brat pans shall have a tilt cut-off device.|
|Fryers||Each pan shall:
The over-temperature device shall:
Note: The above requirements are for guidance only; additional requirements may be applicable to some appliances, or types of appliance, and ESV can advise on the requirements for acceptance.
Note: An exemption from the requirements may be sought from ESV if it is not technically or financially feasible to fit the safety device, but if the appliance was originally supplied with a safety device, it must be operational.
If further information is required, please phone the Gas Safety Technical Information Line on 1800 652 563.